This retrofit converts an existing constant volume multizone HVAC system (MZ–CV) to a variable volume (MZ–VV) system for increased energy efficiency. The technique makes limited changes in instrumentation and uses a novel control scheme to reduce fan speed and coil use when not needed. A demand controlled ventilation option also reduces ventilation when spaces are unoccupied. The retrofit is significantly less expensive and less disruptive than a full system change-out (to VAV). This retrofit can be an interim solution to meet energy reduction targets and accrue savings now while postponing large capital investment. Field demonstration found 24–60% energy savings at the air handler. Typical applications are expected to pay back in 3–5 yrs.
A suite of design and implementation support tools steps a potential user through technology evaluation, procurement, and performance verification. The files are numbered roughly in the probable order of use. Pertinent document formats (including PDF , Excel spreadsheet , Word document , PowerPoint , and AutoCAD drawing files (zipped) ) allow rapid system analyses and development of procurement packages.
|01- Multizone to Variable Volume Overview Fact Sheet||02-17-2022|
|02- Multizone to Variable Volume Technical Note||04-14-2022|
|03- Multizone to Variable Volume Savings Estimator||08-01-2022||XLSX|
|04- Multizone to Variable Volume Pitch Briefing||04-07-2022||PPTX|
|05- Multizone to Variable Volume Scoping Guide||04-05-2022||XLSX|
|06- Multizone to Variable Volume Design Guide with Performance Work Statement, Specifications Book, and Sequences of Operation||04-13-2022||DOCX|
|07- Multizone to Variable Volume Points Schedules||02-15-2022||XLSX|
|08.1- Multizone to Variable Volume Bypass Unit Controls Drawings||02-14-2022|
|08.2- Multizone to Variable Volume Conventional Unit Controls Drawings||02-14-2022|
|08.3- Multizone to Variable Volume Neutral Deck Unit Controls Drawings||02-14-2022|
|09- Multizone to Variable Volume Commissioning Guide||04-05-2022||XLSX|
|10.1- Multizone to Variable Volume Bypass Unit AutoCAD Drawings (12 files)||02-14-2022||DWG/ZIP|
|10.2- Multizone to Variable Volume Conventional Unit AutoCAD Drawings (12 files)||02-14-2022||DWG/ZIP|
|10.3- Multizone to Variable Volume Neutral Deck Unit AutoCAD Drawings (12 files)||02-14-2022||DWG/ZIP|
A technology field demonstration was conducted, and these design and implementation technology transfer tools were developed by the Engineer Research and Development Center, Construction Engineering Research Laboratory (ERDC-CERL) under the DoD Environmental Security Technology Certification Program (ESTCP).