- Aesthetic Challenges
- Aesthetic Opportunities
- Air Barrier Systems in Buildings
- Air Decontamination
- Assessment Tools for Accessibility
- Balancing Security/Safety and Sustainability Objectives
- Building Integrated Photovoltaics (BIPV)
- Cool Metal Roofing
- Designing Buildings to Resist Explosive Threats
- Distributed Energy Resources (DER)
- Electric Lighting Controls
- Electrical Safety
- Energy Analysis Tools
- Energy Codes and Standards
- Energy Efficient Lighting
- Evaluating and Selecting Green Products
- Extensive Vegetative Roofs
- Facility Performance Evaluation (FPE)
- Fuel Cells and Renewable Hydrogen
- Glazing Hazard Mitigation
- High-Performance HVAC
- Life-Cycle Cost Analysis (LCCA)
- Mold and Moisture Dynamics
- Natural Ventilation
- Passive Solar Heating
- Playground Design and Equipment
- Psychosocial Value of Space
- Reliability-Centered Maintenance (RCM)
- Retrofitting Existing Buildings to Resist Explosive Threats
- Security and Safety in Laboratories
- Seismic Design Principles
- Solar Water Heating
- Sun Control and Shading Devices
- Sustainable Laboratory Design
- Sustainable O&M Practices
- The Changing Nature of Organizations, Work, and Workplace
- Therapeutic Environments
- Threat/Vulnerability Assessments and Risk Analysis
- Water Conservation
- Windows and Glazing
Assure Reliable Systems and Spaces
Last updated: 11-03-2011
Within This Page
Reliability is a great concern for building occupants and organizations. Absence of reliability directly affects personal security and well-being, as well as mission critical work. As workplaces evolve in response to changes in organizational structure and work practices, reliability needs to take into consideration the multiplicity of spaces that support individual and group activities. This applies to all facilities whether public or private, institutional or commercial, large or small, regardless of location, circumstance, and/or purpose. Organizations and the occupants of their buildings are entitled to work places that enable them to remain productive and in-touch at all times. Further, there are financial implications of time lost when systems fail and the workspace is not conducive to occupant productivity. Down time does adversely affect the bottom line.
People increasingly expect work settings to fully support pursuit of individual, team, and organizational objectives without operational uncertainty. Building and information systems that disrupt workflow will not be tolerated. The workforce of the future will demand workspace and tools that amplify their abilities and help them do their best to compete effectively. This calls for systems that perform reliably with good maintenance support.
Building users must be able to rely on facility hardware and software for health, life, safety, power, data, and voice delivery systems (and related equipment and tools). These systems need to function consistently and be properly maintained. When the workplace is supported by high-performance systems that require appropriate levels of maintenance to minimize downtime and have back-up capabilities to ensure negligible loss of service, worker productivity can be improved or maintained.
- Employ an integrated design approach and integrated team process during the project planning, design, construction, commissioning and operations processes.
- Provide freestanding (local) system alternatives for individual user access and control.
- Maximize interoperability of different manufacturers' systems and products (including parts interchangeability).
- Provide adequate training and resources to use and/or maintain systems.
- Select systems based on optimum performance, interoperability, and intuitive operation and maintenance.
- Consider dual-fuel back up and onsite renewable energy systems for critical building systems, including fire/emergency, HVAC, lighting, power, data, voice, etc.
- Provide ease of access for maintenance and repair of systems.
- See also WBDG Functional/Operational Branch.
- Maximize conditioning through natural means/methods (e.g. operable windows, natural ventilation, building mass, etc.).
- Consider displacement air supply system that are zoned appropriately for ventilation purposes (e.g., through raised floor system).
- Provide systems with real-time monitoring capability to optimize interaction with building management/maintenance personnel for long-term, efficient operation.
- Provide networked computerized building systems sensors to monitor and manage control of the following systems: HVAC, energy recovery, lighting, building access, security, fire suppression, and smoke alarm.
- Provide building automation systems that are remotely accessible by facilities managers to determine problem locations and monitor environmental conditions without disturbing workers.
Workers at the Philip Merrill Environmental Center in Annapolis, Maryland, enjoy access to daylight and views from all areas of the building.
- Maximize use of daylighting and related lighting control devices (shades, light shelves, etc.).
- Utilize long-life lamps and quality fixtures.
- Zone power circuits to separate ambient and task lighting.
- Utilize occupancy and light level sensing/control devices to extend lamp life.
- Consider emergency back-up lighting systems (generator, battery, etc.) for critical function areas.
- Consider emerging lighting technologies such as low voltage lighting systems, fiber optics, and light emitting diodes (LEDs) that provide quality lighting with greater reliability.
- Provide building surge protection to safeguard data systems and critical electronic equipment.
- Consider Uninterrupted Power Supply (UPS) or other back-up systems (e.g. solar power systems).
- Consider distributed power systems and alternative energy systems for on-site power generation (e.g. fuel cell, solar, wind, microturbines, geothermal, etc.).
Telecommunication Systems/Equipment (voice/data)
- Support distributed computing (see also WBDG Productive—Integrate Technological Tools).
- Update computer hardware and software periodically.
- Provide interchangeable voice/data cabling (category 5+ or higher, plenum rated).
- Consider telecommunication equipment back-up systems (battery power, etc.).
- Consider wireless systems, where feasible, to promote internal mobility and access to emergency services.
- See also WBDG Productive—Integrate Technological Tools.
- See also WBDG Design Disciplines—Information Technology Engineering.
- Provide identification/verification systems (such as card key, fingerprints, eye scans, etc.) to access and/or control IT, data, space, and property.
- Provide hardwired smoke alarms with back-up battery power.
- Provide low power usage emergency egress lights and LED illuminators with rechargeable battery.
- Provide security systems with back-up capability for emergency signals and communication.
- See also WBDG Secure/Safe Branch.
Fuel cell power plant installation at South County Hospital—Wakefield, RI
(Courtesy of the former UTC Fuel Cells now ClearEdge Power)
Increasing demands for renewable, energy-efficient, and environmentally responsible back-up power sources have lead to advancements in fuel cell technology, solar, wind, hydro, and biomass power systems.
Enterprise Resource Planning (ERP)—the integration of all departments and functions across an agency/company onto a single computer system that can serve all those different departments' particular needs.
Reliability-Centered Maintenance (RCM)—the concept of developing a maintenance scheme based on the reliability of the various components of the system or product in question. Implementing a preventative maintenance program using RCM can greatly reduce the cost of ownership of a product or system.
For most building owners and operators, reliability ranks almost as high as cost as a top "quality indicator" when selecting building systems and equipment. "Problem prone equipment," often selected due to lower first costs, reduces system reliability and is clearly a chief motivator for purchasing quality equipment.
Continuous Commissioning—an ongoing process to resolve operating problems, improve comfort, optimize energy use, and identify retrofits for existing buildings and central plant facilities. Continuous commissioning ensures that the building and systems operate optimally to meet the current requirements, which supports worker effectiveness.
Relevant Codes and Standards
ASTM Standard Classifications and Practices
- ASTM Standards for Whole Building Functionality and Serviceability, 3rd Edition
- E 1334 Rating the Serviceability of a Building or Building-Related Facility
- E 1660 Serviceability of an Office Facility for Support for Office Work
- E 1662 Serviceability of an Office Facility for Sound and Visual Environment
- E 1663 Serviceability of an Office Facility for Typical Office Information Technology
- E 1665 Serviceability of an Office Facility for Facility Protection
- E 1666 Serviceability of an Office Facility for Work Outside Normal Hours or Conditions
- E 1669 Serviceability of an Office Facility for Location, Access, and Wayfinding
- E 1670 Serviceability of an Office Facility for Management of Operations and Maintenance
- E 1679 Setting the Requirements for the Serviceability of a Building or Building-Related Facility
- E 1693 Serviceability of an Office Facility for Protection of Occupant Assets
- E 1700 Serviceability of an Office Facility for Structure and Building Envelope
- E 1701 Serviceability of an Office Facility for Manageability
- E 2320 Serviceability of an Office Facility for Thermal Environment and Indoor Air Conditions
Building / Space Types
- Commissioning the Whole Building Enclosure, Journal of Building Enclosure Design, (PDF 3.08 MB) National Institute of Building Sciences, Winter 2008.
- The Integrated Workplace: A Comprehensive Approach to Developing Workspace by Office of Real Property in the Office of Government-wide Policy of the U.S. General Services Administration. May 1999.
- NASA Reliability Centered Maintenance Guide for Facilities and Collateral Equipment
- Nature's Power on Demand: Renewable Energy Systems as Emergency Power Sources by Roberta F. Stauffer. The National Center for Appropriate Technology, October 1995.
- Reliability-Centered Maintenance, 2nd Edition by John Moubray. Industrial Press, 2001. ISBN: 0831131462.
- Renewable and Distributed Energy as a Security Tactic, Energy Chapter 75 of Solutions for Energy Security & Facility Management Challenges, Proceedings of the 25th World Energy Engineering Congress 2003.
- Whole Building Commissioning Process Manual (PDF 11.50 MB), Department of Veterans Affairs, Office of Construction and Facilities Management. August 2010.
- Workplace Matters (PDF 3.61 MB), Public Buildings Service, of the U.S. General Services Administration, 2006.
- Building Commissioning Association
- Center for the Built Environment, University of California at Berkeley, The Contribution of Building Design and Operation to Productivity
- Center for Building Performance and Diagnostics, The Intelligent Workplace, Carnegie Mellon University
- Enterprise Resource Planning (ERP) and Supply Chain Management (SCM) I.T. Works' Reference Site